Computer Manufacturer Facility Root Cause Analysis
BVR Performed in depth electrical system analysis. Arc flash, short circuit, and coordination study. Identified issues eliminating possible safety hazards, and prevented unscheduled downtime. Arc flash labels where generated to further improve safety and meet industry standards. Easy power Modeling was implemented to digitally test all electrical grids on site. Facility now meets all electrical standards, and safety has been drastically improved.